This information is provided free of charge by the Department of Industrial Relations
from its web site at www.dir.ca.gov
. These regulations are for the
convenience of the user and no representation or warranty is made that the information
is current or accurate. See full disclaimer at https://www.dir.ca.gov/od_pub/disclaimer.html
Subchapter 5. Electrical Safety Orders
Group 2. High-Voltage Electrical Safety Orders
Article 36. Work Procedures and Operating Procedures (Refs & Annos)
Return to index
Insulated parts of Live Line Tools shall have manufacturers' certification to withstand the following minimum tests:
(1) 100,000 volts per foot of length for five minutes when the tool is made of fiberglass; or
(2) 75,000 volts per foot of length for three minutes when the tool is made of wood; or
(3) other tests equivalent to (1) or (2) above as appropriate.
Note: Authority cited: Section 142.3, Labor Code. Reference: Section 142.3, Labor Code.
1. Amendment filed 12-10-87; operative 1-9-88 (Register 88, No. 1).
Go Back to Article 36 Table of Contents