|This information is provided free of charge by the Department of Industrial Relations from its web site at www.dir.ca.gov. These regulations are for the convenience of the user and no representation or warranty is made that the information is current or accurate. See full disclaimer at http://www.dir.ca.gov/od_pub/disclaimer.html.|
| Return to index
No welded repair shall be made to any boiler or boiler appurtenance until the welding procedure and operator have been qualified in accordance with Section IX of the code in the overhead and horizontal positions. The certificate of competency number of the qualified inspector authorizing the repair shall be stamped adjacent to all welded repairs made to power boilers.
On welded repairs that are completely radiographed the operator qualification may be eliminated at the discretion of the division provided the welding procedure is properly qualified inspector indicates on his report the welding procedure used and the operator employed in making the repair.
Go Back to Article 7 Table of Contents