| Return to index
Switches used for studio stage set lighting and effects (on the stages and lots and on location) shall be of the externally operable type. Where contactors are used as the disconnecting means for fuses, an individual externally operable switch, such as a tumbler switch, for the control of each contactor shall be located at a distance of not more than 6 feet from the contactor, in addition to remote-control switches.
EXCEPTION: A single externally operable switch shall be permitted to simultaneously disconnect all the contactors on any one location board, where located at a distance of not more than 6 feet from the location board.
(Title 24, Part 3, Section 530-13.)
NOTE: Authority cited: Section 142.3, Labor Code. Reference: Section 142.3, Labor Code; and Section 18943(c), Health and Safety Code.
1. Editorial correction filed 11-2-83 (Register 83, No. 45).
2. Amendment filed 8-27-86; effective thirtieth day thereafter (Register 86, No. 37).