This information is provided free of charge by the Department of Industrial Relations
from its web site at www.dir.ca.gov
. These regulations are for the
convenience of the user and no representation or warranty is made that the information
is current or accurate. See full disclaimer at https://www.dir.ca.gov/od_pub/disclaimer.html
Subchapter 5. Electrical Safety Orders
Group 1. Low-Voltage Electrical Safety Orders
ARTICLE 9. SERVICES
Return to index
§2380.1. Disconnecting Means.
(a) Means shall be provided to disconnect all conductors in a building or other structure from the service-entrance conductors. The service disconnecting means shall plainly indicate whether it is in the open or closed position and shall be installed at a readily accessible location nearest the point of entrance of the service-entrance conductors.
(b) Each service disconnecting means shall simultaneously disconnect all ungrounded conductors.
(c) Each service disconnecting means shall be suitable for the prevailing conditions.
Note: Authority cited: Section 142.3, Labor Code. Reference: Section 142.3, Labor Code.
1. New article 9 (section 2380.1) and section filed 5-5-2008; operative 5-5-2008. Submitted to OAL for printing only pursuant to Labor Code 142.3(a)(3) (Register 2008, No. 19). For prior history of article 9, see Register 79, No. 32.
Go Back to Article 8 Table of Contents