|This information is provided free of charge by the Department of Industrial Relations from its web site at www.dir.ca.gov. These regulations are for the convenience of the user and no representation or warranty is made that the information is current or accurate. See full disclaimer at http://www.dir.ca.gov/od_pub/disclaimer.html.|
| Return to index
(a) Trailing electric power cables shall be maintained in good repair.
(b) Conductors of trailing electric power cables shall be so spliced or joined as to be mechanically and electrically secured without solder and unless an approved splicing device is used, shall then be soldered with a fusible metal or alloy or brazed or welded. All splices and joints and free ends of conductors shall be covered with an insulation equivalent to that on the conductors.
(c) When the jackets of trailing electric power cables have been cut or damaged so that their insulation protection is substantially reduced, or when the conductors of such cables have been sliced, the jackets shall be repaired and vulcanized so that the repaired section will have insulating properties equivalent to the original electric cable cover.
Go Back to the Mine Safety Orders, Article 47 Table of Contents