This information is provided free of charge by the Department of Industrial Relations
from its web site at www.dir.ca.gov
. These regulations are for the
convenience of the user and no representation or warranty is made that the information
is current or accurate. See full disclaimer at https://www.dir.ca.gov/od_pub/disclaimer.html
Subchapter 5. Electrical Safety Orders
Group 2. High-Voltage Electrical Safety Orders
ARTICLE 17. ENCLOSURES FOR ELECTRICAL INSTALLATIONS
§2813. Underground Vaults.
Except to the extent that the following subsections (a) and (b) provide otherwise, manholes or underground rooms in which it may be necessary for persons to work shall comply with Division 4, Sections 8051
through 8057 of the California Public Utilities Code
, which is hereby incorporated by reference:
(a) The inside measurement shall be not less than 4 feet between the end walls and between the side walls thereof, or if circular in shape, not less than 4 feet in diameter inside measurement, and not less than 6 1/2 feet at all points between the floor and the top or ceiling.
(b) Any access opening to outer air shall be not less than 26 inches if circular in shape, or not less than 24 inches by 26 inches clear measurement if rectangular in shape.
1. Editorial correction filed 11-2-83 (Register 83, No. 45).
2. Amendment filed 12-10-87; operative 1-9-88 (Register 88, No. 1).
3. Amendment of first paragraph and repealer of last paragraph filed 12-9-2010; operative 1-8-2011 (Register 2010, No. 50).
Go Back to Article 17 Table of Contents