This information is provided free of charge by the Department of Industrial Relations
from its web site at www.dir.ca.gov
. These regulations are for the
convenience of the user and no representation or warranty is made that the information
is current or accurate. See full disclaimer at https://www.dir.ca.gov/od_pub/disclaimer.html
Subchapter 5. Electrical Safety Orders
Group 2. High-Voltage Electrical Safety Orders
Article 15. Temporary Wiring
§2799.2. Branch Circuits.
The following requirements apply to branch circuits:
(a) Branch circuits shall originate in an approved panelboard.
(b) Conductors shall be multiconductor cord or cable assemblies or open conductors.
(c) No branch-circuit conductor may be laid on the floor.
(d) Each branch circuit that supplies fixed equipment shall contain a separate equipment grounding conductor if run as open conductors.
<General Materials (GM) - References, Annotations, or Tables>
Note: Authority cited: Section 142.3, Labor Code. Reference: Section 142.3, Labor Code
1. New section filed 4-1-2009; operative 4-1-2009. Submitted to OAL for
printing only pursuant to Labor Code section 142.3 (Register 2009, No.
Go Back to Article 15 Table of Contents