| Return to index
Each bus run shall be provided with a permanent nameplate on which the following information shall be provided:
(a) Rated voltage.
(b) Rated continuous current; if bus is forced cooled, both the normal forced cooled rating and the self-cooled (not forced cooled) rating for the same temperature rise shall be given.
(c) Rated frequency.
(d) Rated impulse withstand voltage.
(e) Rated 60-cycle withstand voltage (dry).
(f) Rated momentary current.
(g) Manufacturer's name and address.
NOTE: Metal-enclosed buses shall be constructed and tested in accordance with ANSI C37.20--1969.
(Title 24, Part 3, Section 364-21.)
NOTE: Authority cited: Section 142.3, Labor Code. Reference: Section 142.3, Labor Code; and Section 18943(c), Health and Safety Code.
1. Editorial correction filed 11-2-83 (Register 83, No. 45).
2. Editorial correction filed 11-3-83 (Register 83, No. 45).