(a) Motors and appliances.
(b) Services, feeders, and branch circuits. Each service, feeder, and branch circuit, at its disconnecting means or overcurrent device, shall be legibly marked to indicate its purpose, unless located and arranged so the purpose is evident.
(c) Durability of markings. The markings required by subsections (a) and (b) of this section shall be of sufficient durability to withstand the environment involved.
(d) Capable of accepting a lock. Disconnecting means required by these Electrical Safety Orders shall be capable of being locked in the open position.
(e) Marking for series combination ratings.
(1) Where circuit breakers or fuses are applied in compliance with the series combination ratings marked on the equipment by the manufacturer, the equipment enclosures shall be legibly marked in the field to indicate that the equipment has been applied with a series combination rating.
(2) The marking required by subsection (e)(1) of this section shall be readily visible and shall state “Caution - Series Combination System Rated - Amperes. Identified Replacement Component Required.”