This information is provided free of charge by the Department of Industrial Relations
from its web site at www.dir.ca.gov. These regulations are for the
convenience of the user and no representation or warranty is made that the information
is current or accurate. See full disclaimer at http://www.dir.ca.gov/od_pub/disclaimer.html.
Subchapter 5. Electrical Safety Orders
Group 1. Low-Voltage Electrical Safety Orders
ARTICLE 9. SERVICES
§2380.1. Disconnecting Means.
(a) Means shall be provided to disconnect all conductors in a building or other structure from the service-entrance conductors. The service disconnecting means shall plainly indicate whether it is in the open or closed position and shall be installed at a readily accessible location nearest the point of entrance of the service-entrance conductors.
(b) Each service disconnecting means shall simultaneously disconnect all ungrounded conductors.
(c) Each service disconnecting means shall be suitable for the prevailing conditions.
|| Note: Authority cited: Section 142.3, Labor Code. Reference: Section 142.3, Labor Code.
1. New article 9 (section 2380.1) and section filed 5-5-2008; operative 5-5-2008. Submitted to OAL for printing only pursuant to Labor Code142.3(a)(3) (Register 2008, No. 19). For prior history of article 9, see Register 79, No. 32.
Go Back to Article 8 Table of Contents