|This information is provided free of charge by the Department of Industrial Relations from its web site at www.dir.ca.gov. These regulations are for the convenience of the user and no representation or warranty is made that the information is current or accurate. See full disclaimer at http://www.dir.ca.gov/od_pub/disclaimer.html.|
| Return to index
Audiometric Test Rooms
Rooms used for audiometric testing shall not have background sound pressure levels exceeding those in Table C-1 when measured by equipment conforming at least to the Type 2 requirements of ANSI S1.4-1971 (R1976), and to the Class II requirements of ANSI S1.11-1971 (R1976).
Table C-1 Maximum Allowable Octave-Band Sound Pressure Levels for Audiometric Test Rooms Octave-band center frequency (Hz)............... 500 1000 2000 4000 8000 Sound pressure level (dB)..... 40 40 47 57 62
NOTE: Authority and reference cited: Section 142.3, Labor Code.
1. Amendment filed 10-3-83; effective thirtieth day thereafter (Register 83, No. 41).
Go Back to Article 105 Table of Contents