|This information is provided free of charge by the Department of Industrial Relations from its web site at www.dir.ca.gov. These regulations are for the convenience of the user and no representation or warranty is made that the information is current or accurate. See full disclaimer at http://www.dir.ca.gov/od_pub/disclaimer.html.|
| Return to index
(a) Scope and Application. This Section applies to all water-spray fixed extinguishing systems and to all foam-water sprinkler systems. This Section does not apply to automatic sprinkler systems which are covered in Article 159.
When water-spray fixed systems or foam-water sprinkler systems are provided, they shall meet the design requirements of the National Fire Protection Association's (NFPA) standards on "Water Spray Fixed Systems for Fire Protection" or "Foam-Water Spray Systems," NFPA Nos. 15-1977 or 16-1974, respectively. The systems shall also comply with Article 160.
(b) General Requirements.
(1) The employer shall assure that foam and water spray systems are designed to be effective in at least controlling fire in the protected area or on protected equipment.
(2) The employer shall assure that drainage of water spray systems is directed away from areas where employees are working and that no emergency egress is permitted through the drainage path.
NOTE: Authority and reference cited: Section 142.3, Labor Code.
1. Repealer of Article 163 (Section 6183) and new Article 163 (Section 6182) filed 9-8-81; effective thirtieth day thereafter (Register 81, No. 37). or prior history, see Register 76, No. 29.
2. Change without regulatory effect deleting Title 24 reference (Register 87, No. 49).
Go Back to Article 163 Table of Contents