(a) Rooms in which flammable or combustible liquids are stored or handled by pumps, shall have exit facilities arranged to prevent occupants being trapped in the event of fire.
(b) Rooms in which Category 1 or 2 flammable liquids, or Category 3 flammable liquids with a flashpoint below 100oF (37.8oC) are stored or handled shall be heated only by means not constituting a source of ignition, such as steam or hot water. Rooms containing heating appliances involving sources of ignition shall be located and arranged to prevent entry of flammable vapors.
Note: Authority cited: Section 142.3, Labor Code. Reference: Section 142.3, Labor Code.
1. Amendment filed 7-16-76; effective thirtieth day thereafter (Register 76, No. 29).
2. Amendment of subsection (b) and new Note filed 5-5-2014; operative 5-6-2014 pursuant to Government Code section 11343.4(b)(3) (Register 2014, No. 19).