|This information is provided free of charge by the Department of Industrial Relations from its web site at www.dir.ca.gov. These regulations are for the convenience of the user and no representation or warranty is made that the information is current or accurate. See full disclaimer at http://www.dir.ca.gov/od_pub/disclaimer.html.|
| Return to index
(a) Piping, tubing and fittings shall be suitable for oxygen service and for the pressures and temperatures involved.
(b) Piping and tubing installed after May 30, 1999, shall conform to ASME B31.3-1996, Process Piping, which is hereby incorporated by reference. Piping and tubing installed on or before May 30, 1999, shall conform to either the American National Standard Code for Pressure Piping, Petroleum Refinery Piping, ANSI B31.3-1973, or the updated version of the ANSI/ASME B31.3 standard in effect at the time of installation.
(c) Piping or tubing for operating temperatures below -20o F. shall be fabricated from materials meeting the impact test requirements of Paragraph UG-84 of ASME Boiler and Pressure Vessel Code, Section VIII Unfired Pressure Vessels (1974), when tested at the minimum operating temperature to which the piping may be subjected in service.
Note: Some materials suitable for low temperature piping are austenitic chromium-nickel alloy steels, copper, copper-silicon alloys, aluminum, and some brasses and bronzes.
Authority cited: Section 142.3, Labor Code. Reference: Section 142.3, Labor Code.
1. Amendment of subsection (b) and new Note filed 4-30-99; operative 5-30-99 (Register 99, No. 18).
Go Back to Article 139 Table of Contents