|This information is provided free of charge by the Department of Industrial Relations from its web site at www.dir.ca.gov. These regulations are for the convenience of the user and no representation or warranty is made that the information is current or accurate. See full disclaimer at http://www.dir.ca.gov/od_pub/disclaimer.html.|
| Return to index
(a) After installation, all field erected piping shall be tested and proved hydrogen gastight at operating pressure and temperature.
(b) Containers if out of service in excess of one year shall be inspected and tested as outlined in (a). The safety relief devices shall be checked to determine if they are operable and properly set.
Go Back to Article 138 Table of Contents