|This information is provided free of charge by the Department of Industrial Relations from its web site at www.dir.ca.gov. These regulations are for the convenience of the user and no representation or warranty is made that the information is current or accurate. See full disclaimer at http://www.dir.ca.gov/od_pub/disclaimer.html.|
| Return to index
(a) Covers arranged to close automatically in the event of fire shall be actuated by approved automatic devices and shall also be arranged for manual operation.
(b) Covers shall be of substantial noncombustible material or of tin-clad type with enclosing metal applied with locked joints.
NOTE: For the construction of dip tank covers, refer to NFPA 34-1982.
(c) Chains or wire rope shall be used for cover support or operating mechanism where the burning of a cord would interfere with the action of a device.
(d) Where drain boards return drippings to tanks, special means shall be provided to permit the cover to close tightly and prevent water from sprinklers or other sources draining into dip tank in the event of fire.
(e) Covers shall be kept closed when tanks are not in use.
NOTE: Authority cited: Section 142.3, Labor Code. Reference: Section 142.3, Labor Code.
1. Amendment of subsections (b) and (c) filed 12-5-86; effective thirtieth day thereafter (Register 86, No. 51).
Go Back to Article 136 Table of Contents