|This information is provided free of charge by the Department of Industrial Relations from its web site at www.dir.ca.gov. These regulations are for the convenience of the user and no representation or warranty is made that the information is current or accurate. See full disclaimer at http://www.dir.ca.gov/od_pub/disclaimer.html.|
| Return to index
Water shall not be supplied through a continuous connection to the generator except when the generator is provided with an open overflow or automatic water shutoff which will prevent overfilling of the generator. Where a noncontinuous connection is used, the supply line shall terminate not less than two inches above the opening for filling so that the water can be observed as it enters the generator.
NOTE: Authority cited: Section 142.3, Labor Code. Reference: Section 142.3, Labor Code.
1. Amendment filed 7-16-76; effective thirtieth day thereafter (Register 76, No. 29).
2. Amendment filed 6-12-87; operative 7-12-87 (Register 87, No. 26).
Go Back to Article 82 Table of Contents