|This information is provided free of charge by the Department of Industrial Relations from its web site at www.dir.ca.gov. These regulations are for the convenience of the user and no representation or warranty is made that the information is current or accurate. See full disclaimer at http://www.dir.ca.gov/od_pub/disclaimer.html.
Subchapter 5. Electrical Safety Orders
Group 2. High-Voltage Electrical Safety Orders
Article ARTICLE 41. COMMUNICATIONS SYSTEMS
(a) Masts and metal structures supporting antennas shall be permanently and effectively grounded without splice or connection in the grounding conductor.
(b) Transmitters shall be enclosed in a metal frame or grill or separated from the operating space by a barrier, all metallic parts of which are effectively connected to ground. All external metal handles and controls accessible to the operating personnel shall be effectively grounded. Unpowered equipment and
enclosures are considered to be grounded where connected to an attached coaxial cable with an effectively grounded metallic shield.
| || Note: Authority cited: Section 142.3, Labor Code. Reference: Section 142.3, Labor Code. || |
1. New section filed 4-1-2009; operative 4-1-2009. Submitted to OAL for
printing only pursuant to Labor Code section 142.3 (Register 2009, No.
Back to Article 41 Table of Contents