This information is provided free of charge by the Department of Industrial Relations
from its web site at www.dir.ca.gov. These regulations are for the
convenience of the user and no representation or warranty is made that the information
is current or accurate. See full disclaimer at http://www.dir.ca.gov/od_pub/disclaimer.html.
Subchapter 5. Electrical Safety Orders
Group 2. High-Voltage Electrical Safety Orders
Article ARTICLE 41. COMMUNICATIONS SYSTEMS
§2985.1. Equipment Location.
Outdoor metal structures supporting antennas, as well as self-supporting antennas such as vertical rods or dipole structures, shall be located as far away from overhead conductors of electric light and power circuits of over 600 volts nominal as necessary to prevent the antenna or structure from falling into or making accidental contact with such circuits.
| || Note: Authority cited: Section 142.3, Labor Code. Reference: Section 142.3, Labor Code. || |
1. New section filed 4-1-2009; operative 4-1-2009. Submitted to OAL for
printing only pursuant to Labor Code section 142.3 (Register 2009, No.
Back to Article 41 Table of Contents