|This information is provided free of charge by the Department of Industrial Relations from its web site at www.dir.ca.gov. These regulations are for the convenience of the user and no representation or warranty is made that the information is current or accurate. See full disclaimer at http://www.dir.ca.gov/od_pub/disclaimer.html.|
| Return to index
Electric-discharge tubing shall conform to the following:
(a) Support. Tubing shall be adequately supported on noncombustible, nonabsorptive supports.
(Title 24, Part 3, Section 600-33(b).)
(b) Contact with Flammable Material and Other Surfaces. The tubing shall be free from contact with flammable material and shall be located where not normally exposed to physical damage. Where operating in excess of 7.5 kilovolts, the tubing shall be supported on noncombustible, nonabsorptive, insulating supports which maintain a spacing of not less than 1/4 inch between the tubing and the nearest surface.
(Title 24, Part 3, Section 600-33(c).)
NOTE: Authority cited: Section 142.3, Labor Code. Reference: Section 142.3, Labor Code; and Section 18943(c), Health and Safety Code.
1. Editorial correction filed 11-2-83 (Register 83, No. 45).
2. Amendment filed 12-10-87; operative 1-9-88 (Register 88, No. 1).
Go Back to Article 39 Table of Contents