This information is provided free of charge by the Department of Industrial Relations
from its web site at www.dir.ca.gov. These regulations are for the
convenience of the user and no representation or warranty is made that the information
is current or accurate. See full disclaimer at http://www.dir.ca.gov/od_pub/disclaimer.html.
Subchapter 5. Electrical Safety Orders
Group 2. High-Voltage Electrical Safety Orders
Article 32. Mobile and Portable Equipment (Formerly Article 81)
§2910. Power Cable Connections to Mobile Machines.
A metallic enclosure shall be provided on the mobile machine for enclosing the terminals of the power cable. The enclosure shall include provisions for a solid connection for the grounding terminal to effectively ground the machine frame. Ungrounded conductors shall be attached to insulators or terminated in approved high-voltage cable couplers (which include ground wire connectors) of proper voltage and ampere rating. The method of cable termination used shall prevent any strain or pull on the cable from stressing the electrical
connections. The enclosure shall have provision for locking so only authorized and qualified persons may open, and shall be marked "DANGER-HIGH VOLTAGE."
<General Materials (GM) - References, Annotations, or Tables>
| || Note: Authority cited: Section 142.3, Labor Code. Reference: Section 142.3, Labor Code. || |
1. Editorial correction adding NOTE filed 11-2-83 (Register 83, No. 45).
2. Amendment filed 4-1-2009; operative 4-1-2009. Submitted to OAL for printing
only pursuant to Labor Code section 142.3 (Register 2009, No. 14).
Go Back to Article 32 Table of Contents