| Return to index
Motors driving single or multiple d.c. generators supplying a system operating on a cyclic load basis do not require running overcurrent protection, provided that the thermal rating of the a.c. drive motor cannot be exceeded under any operating condition. However, the branch circuit protective device(s), which may be external to the motor, must provide short circuit and locked rotor protection.
NOTE: Authority cited: Section 142.3, Labor Code. Reference: Section 142.3, Labor Code.
1. Editorial correction adding NOTE filed 11-2-83 (Register 83, No. 45).
Go Back to Article 32 Table of Contents