|This information is provided free of charge by the Department of Industrial Relations from its web site at www.dir.ca.gov. These regulations are for the convenience of the user and no representation or warranty is made that the information is current or accurate. See full disclaimer at http://www.dir.ca.gov/od_pub/disclaimer.html.|
| Return to index
Oil-filled cutouts shall have a fault closing rating equal to or greater than the available fault current which can occur at the cutout location, unless suitable interlocks or operating procedures preclude the possibility of closing into a fault.
(Title 24, Part 3, Section 710-21(d)(4).)
NOTE: Authority cited: Section 142.3, Labor Code. Reference: Section 142.3, Labor Code; and Section 18943(c), Health and Safety Code.
1. Editorial correction adding NOTE filed 11-2-83 (Register 83, No. 45).
2. Amendment filed 12-10-87; operative 1-9-88 (Register 88, No. 1).
Go Back to Article 20 Table of Contents