This information is provided free of charge by the Department of Industrial Relations
from its web site at www.dir.ca.gov. These regulations are for the
convenience of the user and no representation or warranty is made that the information
is current or accurate. See full disclaimer at http://www.dir.ca.gov/od_pub/disclaimer.html.
Subchapter 5. Electrical Safety Orders
Group 2. High-Voltage Electrical Safety Orders
ARTICLE 20. INTERRUPTING AND ISOLATING DEVICES
Automatic circuit reclosers shall comply with all the provisions of American National Standard ANSI/IEEE C37.60-1981, Requirements for Overhead, Pad Mounted, Dry Vault, and Submersible Automatic Circuit Reclosers and Fault Interrupters for AC Systems, which is hereby incorporated by reference, and with all the requirements of Article 21, except that the provisions of ANSI/IEEE C37.04-1979 referenced in Article 21 do not apply to circuit reclosers.
(Title 24, Part 3, Section 3-710-21(d)(9).)
<General Materials (GM) - References, Annotations, or Tables>
| || Note: Authority cited: Section 142.3, Labor Code. Reference: Section 142.3, Labor Code; and Section 18943(c), Health and Safety Code. || |
1. Amendment filed 2-1-83; effective thirtieth day thereafter (Register 83,
2. Editorial correction including renumbering of former Article 71 to Article
22 filed 11-2-83 (Register 83, No. 45).
3. Amendment filed 12-10-87; operative 1-9-88 (Register 88, No. 1).
4. Removal of article 22 heading filed 4-1-2009; operative 4-1-2009. Submitted
to OAL for printing only pursuant to Labor Code section 142.3 (Register
2009, No. 14).
Go Back to Article 20 Table of Contents