|This information is provided free of charge by the Department of Industrial Relations from its web site at www.dir.ca.gov. These regulations are for the convenience of the user and no representation or warranty is made that the information is current or accurate. See full disclaimer at http://www.dir.ca.gov/od_pub/disclaimer.html.
Subchapter 5. Electrical Safety Orders
Group 2. High-Voltage Electrical Safety Orders
Article 18. Conductors
§2819. Conductor Terminations.
(a) Where insulated conductors are terminated or spliced, suitable terminations or stress cones shall be installed unless other effective means are used to reduce voltage stress. The metallic shielding or any other voltage shields on cables shall be stripped back to a safe distance according to the circuit voltage and insulation, at all terminations of the shielding, as in potheads and joints.
(b) Moisture or mechanical protection for metal-sheathed cables. Where cable conductors emerge from a metal sheath and where protection against moisture or physical damage is necessary, the insulation of the conductors shall be protected by a cable sheath terminating device.
<General Materials (GM) - References, Annotations, or Tables>
| || Note: Authority cited: Section 142.3, Labor Code. Reference: Section 142.3, Labor Code. || |
1. Editorial correction filed 11-2-83 (Register 83, No. 45).
2. Amendment filed 12-10-87; operative 1-9-88 (Register 88, No. 1).
3. Amendment of section and Note filed 4-1-2009; operative 4-1-2009. Submitted
to OAL for printing only pursuant to Labor Code section 142.3 (Register
2009, No. 14).
Go Back to Article 18 Table of Contents