| Return to index
Conductors in size 1/0 or larger shall be permitted to be run in multiple. Where conductors are run in multiple, they shall be so installed and terminated to prevent overloading of any conductor. Where conductors are run in multiple, the conductors shall be connected together at each end.
(Title 24, Part 3, Section 3-310-4.)
NOTE: Authority cited: Section 142.3, Labor Code. Reference: Section 142.3, Labor Code; and Section 18943(c), Health and Safety Code.
1. Editorial correction filed 11-2-83 (Register 83, No. 45).
2. Amendment filed 12-10-87; operative 1-9-88 (Register 88, No. 1).
Go Back to Article 18 Table of Contents