This information is provided free of charge by the Department of Industrial Relations
from its web site at www.dir.ca.gov. These regulations are for the
convenience of the user and no representation or warranty is made that the information
is current or accurate. See full disclaimer at http://www.dir.ca.gov/od_pub/disclaimer.html.
Subchapter 5. Electrical Safety Orders
Group 2. High-Voltage Electrical Safety Orders
ARTICLE 17. ENCLOSURES FOR ELECTRICAL INSTALLATIONS
§2810. Locked Rooms, Vaults, or Enclosures.
(a) The entrances to enclosures containing exposed high-voltage energized parts shall be kept locked, except where such entrances are at all times under the observation of a qualified attendant. Access doors or gates to rooms, vaults, or fenced enclosures containing electrical equipment shall be readily opened from the inside without the use of a key.
(b) The type of enclosure used in a given case shall be designed and
constructed according to the hazards associated with the installation.
<General Materials (GM) - References, Annotations, or Tables>
| || Note: Authority cited: Section 142.3, Labor Code. Reference: Section 142.3, Labor Code. || |
1. Editorial correction filed 11-2-83 (Register 83, No. 45).
2. Amendment of section and Note filed 4-1-2009; operative 4-1-2009. Submitted
to OAL for printing only pursuant to Labor Code section 142.3 (Register
2009, No. 14).
Go Back to Article 17 Table of Contents