|This information is provided free of charge by the Department of Industrial Relations from its web site at www.dir.ca.gov. These regulations are for the convenience of the user and no representation or warranty is made that the information is current or accurate. See full disclaimer at http://www.dir.ca.gov/od_pub/disclaimer.html.|
| Return to index
No additional enclosure is required for equipment, provided (a) all energized parts and conductors are protected by metallic enclosures from accidental contact, and (b) such enclosures are bonded together and effectively grounded in accordance with Article 6.
(Title 24, Part 3, Section 3-110-40.)
NOTE: Authority cited: Section 142.3, Labor Code. Reference: Section 142.3, Labor Code; and Section 18943(c), Health and Safety Code.
1. Editorial correction filed 11-2-83 (Register 83, No. 45).
Go Back to Article 17 Table of Contents