| Return to index
No additional enclosure is required for equipment, provided (a) all energized parts and conductors are protected by metallic enclosures from accidental contact, and (b) such enclosures are bonded together and effectively grounded in accordance with Article 6.
(Title 24, Part 3, Section 3-110-40.)
NOTE: Authority cited: Section 142.3, Labor Code. Reference: Section 142.3, Labor Code; and Section 18943(c), Health and Safety Code.
1. Editorial correction filed 11-2-83 (Register 83, No. 45).
Go Back to Article 17 Table of Contents