|This information is provided free of charge by the Department of Industrial Relations from its web site at www.dir.ca.gov. These regulations are for the convenience of the user and no representation or warranty is made that the information is current or accurate. See full disclaimer at http://www.dir.ca.gov/od_pub/disclaimer.html.|
| Return to index
Electrical equipment shall be permitted to be installed on the roof of a building, provided:
(a) The building structure has sufficient strength to support the entire installation.
(b) Where oil-insulated equipment is used, the roof shall be of two-hour, non-combustible fire resistive construction, and a curb high enough to contain the oil from the largest oil-filled equipment shall be provided. In no case shall the height of the curb be less than 6 inches. A drain shall be provided from the curbed enclosure to carry any oil which it may contain well away from the building.
(Title 24, Part 3, Section 3-110-39.)
NOTE: Authority cited: Section 142.3, Labor Code. Reference: Section 142.3, Labor Code; and Section 18943(c), Health and Safety Code.
1. Editorial correction filed 11-2-83 (Register 83, No. 45).
2. Amendment filed 12-10-87; operative 1-9-88 (Register 88, No. 1).
Go Back to Article 17 Table of Contents