|This information is provided free of charge by the Department of Industrial Relations from its web site at www.dir.ca.gov. These regulations are for the convenience of the user and no representation or warranty is made that the information is current or accurate. See full disclaimer at http://www.dir.ca.gov/od_pub/disclaimer.html.|
| Return to index
Electrical equipment containing flammable gas or more than 10 gallons of flammable oil per unit shall not be installed indoors except in a vault or a separate building meeting the following requirements:
(a) Neither the building nor its contents present a fire hazard to any other building or property.
(b) The building is used only for supplying electrical service.
(c) The interior is accessible only to qualified persons.
(Title 24, Part 3, Section 3-110-38.)
NOTE: Authority cited: Section 142.3, Labor Code. Reference: Section 142.3, Labor Code; and Section 18943(c), Health and Safety Code.
1. Editorial correction filed 11-2-83 (Register 83, No. 45).
Go Back to Article 17 Table of Contents