|This information is provided free of charge by the Department of Industrial Relations from its web site at www.dir.ca.gov. These regulations are for the convenience of the user and no representation or warranty is made that the information is current or accurate. See full disclaimer at http://www.dir.ca.gov/od_pub/disclaimer.html.|
| Return to index
When a cable is suspended by its conductor(s), the total suspended weight shall not be greater than one-seventh of the ultimate tensile strength of the supporting conductor(s). Cable supports shall be designed to carry adequately the weight of the cable.
Separate supports shall be provided for the sheath of unarmored lead-sheathed cable.
(Title 24, Part 3, Section 3-300-37(a).)
NOTE: Authority cited: Section 142.3, Labor Code. Reference: Section 142.3, Labor Code; and Section 18943(c), Health and Safety Code.
1. Editorial correction including renumbering of former Article 65 to Article 16 filed 11-2-83 (Register 83, No. 45).
Go Back to Article 16 Table of Contents