|This information is provided free of charge by the Department of Industrial Relations from its web site at www.dir.ca.gov. These regulations are for the convenience of the user and no representation or warranty is made that the information is current or accurate. See full disclaimer at http://www.dir.ca.gov/od_pub/disclaimer.html.|
| Return to index
Metal-clad cable shall not be installed below an elevation of 8 fee above working platform or grade without additional mechanical protection.
EXCEPTION: Where the cable terminates in the top of metal-enclosed switchgear, transformers, rotating equipment, and other enclosed equipment, the cable may be extended vertically down to the top of the enclosure if adequate mechanical support is provided.
(Title 24, Part 3, Section 3-334-26.)
NOTE: Authority cited: Section 142.3, Labor Code. Reference: Section 142.3, Labor Code; and Section 18943(c), Health and Safety Code.
1. Editorial correction filed 11-2-83 (Register 83, No. 45).
Go Back to Article 13 Table of Contents