| Return to index
Metal-clad cable shall be permitted to be installed on metal racks, trays, troughs, or continuous rigid cable supports which are effectively grounded. Each cable shall be supported at intervals not exceeding 6 feet and within 2 feet of every box or fitting, and each cable shall be attached to the support at intervals of not more than 10 feet horizontally and 2 feet vertically.
(Title 24, Part 3, Section 3-334-25.)
NOTE: Authority cited: Section 142.3, Labor Code. Reference: Section 142.3, Labor Code; and Section 18943(c), Health and Safety Code.
1. Editorial correction filed 11-2-83 (Register 83, No. 45).
2. Amendment filed 12-10-87; operative 1-9-88 (Register 88, No. 1).