| Return to index
Continuous rigid cable supports shall be permitted to be used as the mechanical support for metal-clad cables in fire-resistive building constructions as permitted in Section 2783, but shall not be used in hoistways, or where subjected to severe physical damage. Continuous rigid cable supports shall be permitted to be used to support metal-clad cables in flammable atmospheres as permitted in Article 34.
(Title 24, Part 3, Sections 3-318-2(a) and 318-3.)
NOTE: Authority cited: Section 142.3, Labor Code. Reference: Section 142.3, Labor Code; and Section 18943(c), Health and Safety Code.
1. Editorial correction filed 11-2-83 (Register 83, No. 45).
2. Editorial correction filed 11-3-83 (Register 83, No. 45).
3. Amendment filed 12-10-87; operative 1-9-88 (Register 88, No. 1).