|This information is provided free of charge by the Department of Industrial Relations from its web site at www.dir.ca.gov. These regulations are for the convenience of the user and no representation or warranty is made that the information is current or accurate. See full disclaimer at http://www.dir.ca.gov/od_pub/disclaimer.html.|
| Return to index
Each bus run shall be provided with a permanent nameplate on which the following information shall be provided:
(a) Rated voltage.
(b) Rated continuous current; if bus is forced cooled, both the normal forced cooled rating and the self-cooled (not forced cooled) rating for the same temperature rise shall be given.
(c) Rated frequency.
(d) Rated impulse withstand voltage.
(e) Rated 60-cycle withstand voltage (dry).
(f) Rated momentary current.
(g) Manufacturer's name and address.
NOTE: Metal-enclosed buses shall be constructed and tested in accordance with ANSI C37.20--1969.
(Title 24, Part 3, Section 364-21.)
NOTE: Authority cited: Section 142.3, Labor Code. Reference: Section 142.3, Labor Code; and Section 18943(c), Health and Safety Code.
1. Editorial correction filed 11-2-83 (Register 83, No. 45).
2. Editorial correction filed 11-3-83 (Register 83, No. 45).
Go Back to Article 11 Table of Contents