| Return to index
The conductor shall not be bent to a radius less than eight times the overall diameter for non-shielded conductors or twelve times the diameter for shielded or lead-covered conductors during or after installation.
(Title 24, Part 3, Sections 300-34.)
NOTE: Authority cited: Section 142.3, Labor Code. Reference: Section 142.3, Labor Code; and Section 18943(c), Health and Safety Code.
1. Editorial correction filed 11-2-83 (Register 83, No. 45).
2. Amendment filed 12-10-87; operative 1-9-88 (Register 88, No. 1).