| Return to index
Each feeder shall be arranged so that it can be isolated from all sources of supply except that isolating switches are not required for taps. Isolating switches shall meet the requirements of Articles 20 or 21.
(Title 24, Part 3, Section 3-710-24(r).)
NOTE: Authority cited: Section 142.3, Labor Code. Reference: Section 142.3, Labor Code; and Section 18943(c), Health and Safety Code.
1. Editorial correction filed 11-2-83 (Register 83, No. 45).
Go Back to Article 5 Table of Contents