|This information is provided free of charge by the Department of Industrial Relations from its web site at www.dir.ca.gov. These regulations are for the convenience of the user and no representation or warranty is made that the information is current or accurate. See full disclaimer at http://www.dir.ca.gov/od_pub/disclaimer.html.|
| Return to index
Each feeder shall be arranged so that it can be isolated from all sources of supply except that isolating switches are not required for taps. Isolating switches shall meet the requirements of Articles 20 or 21.
(Title 24, Part 3, Section 3-710-24(r).)
NOTE: Authority cited: Section 142.3, Labor Code. Reference: Section 142.3, Labor Code; and Section 18943(c), Health and Safety Code.
1. Editorial correction filed 11-2-83 (Register 83, No. 45).
Go Back to Article 5 Table of Contents