|This information is provided free of charge by the Department of Industrial Relations from its web site at www.dir.ca.gov. These regulations are for the convenience of the user and no representation or warranty is made that the information is current or accurate. See full disclaimer at http://www.dir.ca.gov/od_pub/disclaimer.html.|
| Return to index
A switch meeting the requirements of these regulations shall be installed on the source end of each feeder or branch circuit.
(a) Paralleling Switches.
(1) Two or more feeders which can be operated in a parallel shall be provided with a suitable switch(es) to isolate each feeder from all other feeders.
(2) The switch(es) intended to make and break parallel shall conform to Article 20 or 21.
(3) Operation of paralleling switches shall be restricted to qualified and authorized persons only. A written switching procedure shall be made available to and followed by such personnel.
(Title 24, Part 3, Section 3-710-24(r).)
NOTE: Authority cited: Section 142.3, Labor Code. Reference: Section 142.3, Labor Code; and Section 18943(c), Health and Safety Code.
1. Editorial correction filed 11-2-83 (Register 83, No. 45).
Go Back to Article 5 Table of Contents