|This information is provided free of charge by the Department of Industrial Relations from its web site at www.dir.ca.gov. These regulations are for the convenience of the user and no representation or warranty is made that the information is current or accurate. See full disclaimer at http://www.dir.ca.gov/od_pub/disclaimer.html.|
| Return to index
A means conforming to Article 20 or 21 shall be provided to isolate the load and each overcurrent protective device in the service entrance conductors from all sources of supply.
(Title 24, Part 3, Section 3-230-215.)
NOTE: Authority cited: Section 142.3, Labor Code. Reference:Section 142.3, Labor Code; and Section 18943(c), Health and Safety Code.
1. Editorial correction filed 11-2-83 (Register 83, No. 45).
2. Amendment filed 12-10-87; operative 1-9-88 (Register 88, No. 1).
Go Back to Article 4 Table of Contents