|This information is provided free of charge by the Department of Industrial Relations from its web site at www.dir.ca.gov. These regulations are for the convenience of the user and no representation or warranty is made that the information is current or accurate. See full disclaimer at http://www.dir.ca.gov/od_pub/disclaimer.html.
Subchapter 5. Electrical Safety Orders
Group 2. High-Voltage Electrical Safety Orders
Article 4. Service and Service Entrance Equipment
§2725. Location of Switching Devices and Other Service Entrance Equipment.
(a) Means shall be provided to disconnect all conductors in a building or other structure from the service-entrance conductors. The service disconnecting means shall plainly indicate whether it is in the open or closed position and shall be installed at a readily accessible location nearest the point of entrance of the service-entrance conductors.
(b) The service disconnecting means shall simultaneously disconnect all
ungrounded conductors supplied through the service entrance conductors.
Exception: No. 1: Metering equipment shall be permitted to be placed on the source side of the service switching device and fuses, provided the metering is suitably enclosed and no energized parts or wiring are exposed or accessible to other than employees of the serving agency.
Exception: No. 2: Current transformers for protection of service equipment or current indication.No. 2: Current transformers for protection of service equipment or current indication.
Exception: No. 3: When suitable overcurrent protection and disconnecting means are provided, a circuit used for any of the following purposes shall be permitted to also be connected on the source side of the service entrance switching device: (a) Fire pumps; and (b) Potential or control transformers for electrical operation or protection of the service equipment, or for voltage indication. If voltage indication is provided, it shall be on all phases.
(c) Surge and lightning protection equipment shall be connected to the source side of switching devices.
(d) Each service disconnecting means shall be suitable for the prevailing conditions.
<General Materials (GM) - References, Annotations, or Tables>
| || Note: Authority cited: Section 142.3, Labor Code. Reference: Section 142.3, Labor Code. || |
1. Editorial correction filed 11-2-83 (Register 83, No. 45).
2. Amendment filed 12-10-87; operative 1-9-88 (Register 88, No. 1).
3. Amendment of section and Note filed 4-1-2009; operative 4-1-2009. Submitted
to OAL for printing only pursuant to Labor Code section 142.3 (Register
2009, No. 14).
Go Back to Article 4 Table of Contents