| Return to index
Installations covered by this Article shall comply with all applicable provisions of these Safety Orders, except as follows:
(a) Overcurrent protection of electrolytic cell dc process power circuits need not comply with the requirements of Article 10, Overcurrent Protection;
(b) Equipment located or used within the cell line working zone or associated with the cell line dc power circuits need not comply with the provisions of Article 11, Grounding; and
(c) Electrolytic cells, cell line conductors, cell line attachments, and the wiring of auxiliary equipment and devices within the cell line working zone need not comply with the provisions of Article 2. Administration, Article 6, Branch Circuits, or Article 8, Outdoor Wiring.
Note: Authority cited: Section 142.3, Labor Code. Reference: Section 142.3, Labor Code.
1. New section filed 5-5-2008; operative 5-5-2008. Submitted to OAL for printing only pursuant to Labor Code 142.3(a)(3) (Register 2008, No. 19).
Go Back to Article 83 Table of Contents