|This information is provided free of charge by the Department of Industrial Relations from its web site at www.dir.ca.gov. These regulations are for the convenience of the user and no representation or warranty is made that the information is current or accurate. See full disclaimer at http://www.dir.ca.gov/od_pub/disclaimer.html.|
| Return to index
(a) Flexible cords used with the following equipment may not exceed 3 feet (0.9 m) in length and shall have a copper equipment grounding conductor with a grounding-type attachment plug.
(1) Cord- and plug-connected lighting fixtures installed within 16 feet (4.88 m) of the water surface of permanently installed pools.
(2) Other cord- and plug-connected, fixed or stationary equipment used with permanently installed pools.
Note: Authority cited: Section 142.3, Labor Code. Reference: Section 142.3, Labor Code.
1. New section filed 8-27-86; effective thirtieth day thereafter (Register 86, No. 37).
2. Amendment of section and Note filed 5-5-2008; operative 5-5-2008. Submitted to OAL for printing only pursuant to Labor Code 142.3(a)(3) (Register 2008, No. 19).
Go Back to Article 79 Table of Contents