| Return to index
Conductors of different systems grouped in the same conduit or other metal enclosure or in portable cords or cables shall comply with (a) through (c) below.
(a) Power-Supply Conductors. Power-supply conductors shall be properly identified and shall be used solely for supplying power to the equipment to which the other conductors are connected.
(b) Leads to Motor Generator or Rotary Converter. Input leads to a motor generator or rotary converter shall be run separately from the output leads.
(c) Conductor Insulation. The conductors shall be insulated individually, or collectively in groups, by insulation at least equivalent to that on the power supply and other conductors.
EXCEPTION: Where the power supply and other conductors are separated by a lead sheath or other continuous metallic covering.
(Title 24, Part 3, Section 640-6.)
NOTE: Authority cited: Section 142.3, Labor Code. Reference: Section 142.3, Labor Code; and Section 18943(c), Health and Safety Code.
1. Editorial correction filed 11-2-83 (Register 83, No. 45).
Go Back to Article 76 Table of Contents