| Return to index
Cable connectors, male and female, for flexible conductors shall be so constructed that tension on the cord or cable will not be transmitted to the connections. The female half of the connector shall be attached to the load end of the power cord or cable. The connector shall be rated in amperes and designed so that differently rated devices cannot be connected together. (See Section 2500.10 for pull at terminals.)
(Title 24, Part 3, Section 520-67.)
NOTE: Authority cited: Section 142.3, Labor Code. Reference: Section 142.3, Labor Code; and Section 18943(c), Health and Safety Code.
1. Editorial correction filed 11-2-83 (Register 83, No. 45).
2. Amendment filed 8-27-86; effective thirtieth day thereafter (Register 86, No. 37).
Go Back to Article 70 Table of Contents