| Return to index
Circuits from portable switchboards directly supplying equipment containing incandescent lamps of not over 300 watts shall be protected by overcurrent devices having a rating or setting of not over 20 amperes. Circuits for lampholders over 300 watts shall be permitted where overcurrent protection complies with Article 10. Other circuits shall be provided with overcurrent devices with a rating or setting not higher than the current required for the connected load.
(Title 24, Part 3, Section 520-52.)
NOTE: Authority cited: Section 142.3, Labor Code. Reference: Section 142.3, Labor Code; and Section 18943(c), Health and Safety Code.
1. Editorial correction filed 11-2-83 (Register 83, No. 45).
2. Amendment deleting subsection (a) designation only filed 8-27-86; effective thirtieth day thereafter (Register 86, No. 37).
Go Back to Article 70 Table of Contents