This information is provided free of charge by the Department of Industrial Relations
from its web site at www.dir.ca.gov. These regulations are for the
convenience of the user and no representation or warranty is made that the information
is current or accurate. See full disclaimer at http://www.dir.ca.gov/od_pub/disclaimer.html.
Subchapter 5. Electrical Safety Orders
Group 1. Low-Voltage Electrical Safety Orders
Article 58. Capacitors
§2534.8. Disconnecting Means.
A disconnecting means shall be provided in each ungrounded conductor for each capacitor bank and shall meet the following requirements:
(a) The disconnecting means shall open all ungrounded conductors simultaneously.
(b) The disconnecting means shall be permitted to disconnect the capacitor from the line as a regular operating procedure.
(c) The rating of the disconnecting means shall not be less than 135 percent of the rated current of the capacitor.
Exception: A separate disconnecting means shall not be required where a capacitor is connected on the load side of a motor controller.
1. Editorial correction filed 11-2-83 (Register 83, No. 45).
2. Amendment of Title 24 cross reference filed 8-27-86; effective thirtieth day thereafter (Register 86, No. 37).
3. Amendment of section and Note filed 5-5-2008; operative 5-5-2008. Submitted to OAL for printing only pursuant to Labor Code 142.3(a)(3)
(Register 2008, No. 19).
4. Amendment filed 4-6-2010; operative 5-6-2010 (Register 2010, No. 15).
Go Back to Article 58 Table of Contents