|This information is provided free of charge by the Department of Industrial Relations from its web site at www.dir.ca.gov. These regulations are for the convenience of the user and no representation or warranty is made that the information is current or accurate. See full disclaimer at http://www.dir.ca.gov/od_pub/disclaimer.html.|
| Return to index
(a) If a motor and the driven machinery are not in sight from the controller location, the installation shall comply with one of the following conditions:
(1) The controller disconnecting means shall be capable of being locked in the open position.
(2) A manually operable switch that will disconnect the motor from its source of supply shall be placed in sight from the motor location.
(Title 24, Part 3, Section 430-86.)
NOTE: Authority cited: Section 142.3, Labor Code. Reference: Section 142.3, Labor Code; and Section 18943(c), Health and Safety Code.
1. Editorial correction filed 11-2-83 (Register 83, No. 45).
2. Repealer and new section filed 8-27-86; effective thirtieth day thereafter (Register 86, No. 37).
Go Back to Article 56 Table of Contents