|This information is provided free of charge by the Department of Industrial Relations from its web site at www.dir.ca.gov. These regulations are for the convenience of the user and no representation or warranty is made that the information is current or accurate. See full disclaimer at http://www.dir.ca.gov/od_pub/disclaimer.html.|
| Return to index
The controller shall have a horsepower rating not lower than the horsepower rating of the motor.
EXCEPTION: No. 1: For a stationary motor rated at 2 horsepower or less, and 300 volts or less, the controller shall be permitted to be a general-use switch having an ampere rating not less than twice the full load current rating of the motor.
On AC circuits, general-use snap switches suitable only for use on AC (not general-use AC-DC snap switches) shall be permitted to control a motor rated at 2 horsepower or less and 300 volts or less having a full load current rating not more than 80 percent of the ampere rating of the switch.
EXCEPTION: No. 2: A branch circuit inverse time circuit breaker rated in amperes only shall be permitted as a controller. Where this circuit breaker is also used for overload protection, it shall conform to the appropriate provisions of this Article governing overload protection.
EXCEPTION: No. 3: The motor controller for a torque motor shall have a continuous-duty full load current rating not less than the nameplate current rating of the motor.
(Title 24, Part 3, Section 430-83.)
NOTE: Authority cited: Section 142.3, Labor Code. Reference: Section 142.3, Labor Code; and Section 18943(c), Health and Safety Code.
1. Editorial correction filed 11-2-83 (Register 83, No. 45).
2. Amendment deleting subsection (a) designation only filed 8-27-86; effective thirtieth day thereafter (Register 86, No. 37).
3. Editorial correction of Exception No. 1 (Register 92, No. 15).
Go Back to Article 56 Table of Contents