|This information is provided free of charge by the Department of Industrial Relations from its web site at www.dir.ca.gov. These regulations are for the convenience of the user and no representation or warranty is made that the information is current or accurate. See full disclaimer at http://www.dir.ca.gov/od_pub/disclaimer.html.|
| Return to index
This Section, "Motor Controllers," is intended to require suitable controllers for all motors.
(a) Definition. For definition of "Controller," see Article 1. For the purpose of this Article, the term "Controller" includes any switch or device normally used to start and stop a motor.
(b) Stationary Motor of 1/8 Horsepower or Less. For a stationary motor rated at 1/8 horsepower or less that is normally left running and is so constructed that it cannot be damaged by overload or failure to start, such as clock motors and the like, the branch circuit protective device shall be permitted to serve as the controller.
(c) Portable Motor of 1/3 Horsepower or Less. For a portable motor rated at 1/3 horsepower or less, the controller shall be permitted to be an attachment plug and receptacle.
(Title 24, Part 3, Section 430-81.)
NOTE: Authority cited: Section 142.3, Labor Code. Reference: Section 142.3, Labor Code; and Section 18943(c), Health and Safety Code.
1. Editorial correction filed 11-2-83 (Register 83, No. 45).
Go Back to Article 56 Table of Contents