|This information is provided free of charge by the Department of Industrial Relations from its web site at www.dir.ca.gov. These regulations are for the convenience of the user and no representation or warranty is made that the information is current or accurate. See full disclaimer at http://www.dir.ca.gov/od_pub/disclaimer.html.|
| Return to index
All fixed outdoor electric de-icing and snow melting equipment shall be provided with a means for disconnection from all ungrounded conductors. Where readily accessible to the user of the equipment, the branch circuit switch or circuit breaker shall be permitted to serve as the disconnecting means. Switches used as disconnecting means shall be of the indicating type.
(Title 24, Part 3, Section 426-50.)
NOTE: Authority cited: Section 142.3, Labor Code. Reference: Section 142.3, Labor Code; and Section 18943(c), Health and Safety Code.
1. Renumbering and amendment of former Section 2526.20 to Section 2526.50 filed 8-27-86; effective thirtieth day thereafter (Register 86, No. 37). For history of former section, see Register 83, No. 45.
Go Back to Article 54 Table of Contents